Textile & Spinning Mill
TYPE OF INDUSTRY – Textile & Spinning Mill, Punjab India
YEAR OF IMPLEMENTATION – 2017
- Low power factor
- High KVAH consumption
- Leading Power Factor ( High Rkvah lead )
- Frequent Electrical breakdowns.
- Frequent failure of existing capacitor banks.
- High Monthly Electricity Bills .
After conducting Power Quality Audit in the plant, following observations are made:
Power factor is 0.92 with Existing Fixed Capacitor Banks.
Leading Power Factor which cause high Rkvah lead.
Space inside Plant is not available to install Capacitor Banks.
High Voltage Automatic Controlled Harmonic Filter Banks at 11 KV Main Bus in Open Switch yard.
PF improvement > 998.
More than 7 % Saving in KVAH Consumption.
Rkvah lead controlled to negligible value.
Reduction in Electrical Breakdowns.
Comply with Tariff of PSEB.
Pay back in less than 6 months.